Weather permitting, the Curran Gardner Township Public Water District will be performing necessary maintenance and repairs on Tuesday, February 7 between 9:00 am and 1:00 pm that will affect services to customers at the following locations West of the Farmingdale water tower: Town of Berlin, Farley Road, McQueen Road Booth Road, Wake Road, Old Jacksonville Road West to Wake Road, Wilson Road, Skinner Road, Spring Creek and Crystal Lake Subdivision. Customers may notice a variation of water pressure as well as complete loss of water. ONCE THE REPAIRS HAVE BEEN COMPLETED A BOIL ORDER WILL BE IN EFFECT UNTIL FURTHER NOTICE. web posted Feb. 6, 2017\\\\\
CURRAN GARDNER TOWNSHIP PUBLIC WATER DISTRICT
SYSTEM MATERIAL INVENTORY FOR THE LEAD AND COPPER RULE (LCR)
Due to the events that have occurred in Flint, Michigan regarding the presence of lead in many of its homes and businesses many of our customers are concerned about the quality of their own water.
We want to take this opportunity to inform you our customers about the safety of the water lines in the Curran-Gardner Water District system.
Your water district began water service to a small customer base in 1966. It now provides water to over 2500 homes and businesses. Our distribution system water mains are all constructed of cast-iron, ductile-iron, A/C pipe, or PVC (plastic). None of these mains contain lead in their composition.
Lead in drinking water is usually only found in the service lines that are constructed totally of lead, partially of lead, or copper pipes that were bonded with solder containing lead. Since the installation of lead service lines (either fully or partially) was never done in our district, there is no risk of lead poisoning or even the presence of lead in our water service connections. All of our service lines are made of copper or plastic. Due to our treatment process, we also have an interior coating that prevents lead from lead solder from coming into contact with your drinking water.
The Lead and Copper Rule (LCR) originally required that we collect 40 samples each year for lead and copper analysis. After several testing cycles showed that our district did not have worrisome lead or copper levels, the Illinois EPA lowered our sampling requirements to 20 samples each year. Based on subsequent sampling results, the Illinois EPA reduced our monitoring schedule to 20 samples collected on a three-year collection schedule.
During our last collection/analysis testing cycle 19 of the 20 samples showed no detection of lead at all. One sample did show a level of 5.87 parts per billion. This level is still well below the Action Level for lead (15.00 parts per billion) and we believe is linked to sample collection error.
To learn more about our water system and all testing results, including lead, you can to the Illinois Environmental Protection Agency website at:
Click on “For Citizens” (on left side of home page)
Scroll down to “Drinking Water” (section at bottom middle of page)
Click on “Drinking Water Watch”
Click on “Click Here for the County Map of Illinois”
Click on “Sangamon County”
Click on “Curran-Gardner Townships PWD”
To review our Lead sampling results, click on “Chem/Rad Sample/Results”
(All of our lead samples begin with the ID letters “LP” or “LA”)
To check the individual results of each lead sample site, click on samples beginning with “SG”
This will show you the results of both lead and copper at that particular sample site.
We apologize for the many “clicks” it takes to get to the site but the direct address consists of 66 characters! If you have any questions or comments regarding lead levels or any other topic, please feel free to contact our Operations Manager at 217-820-1561.
For complete information, please visit our website at currangardner.com or call 217/546-3981.
NOTICE OF INTENT TO FILE APPLICATION
The Curran Gardner Townships Public Water District, Sangamon County of Illinois is submitting an application for financial assistance to USDA Rural Development for Water Treatment Plant Expansion.
Additional information may be obtained by visiting currangardner.com or contacting the District administrative office at 217/546-3981.
Curran Gardner Townships Public Water District
3382 Hazlett Road
Springfield, IL 62707
Special Notice to Springfield Sanitary District Customers within the Curran-Gardner Water District service area
At the request of the Springfield Metro Sanitary District, the Curran Gardner Water District has agreed to serve as the billing agent for the Sanitary District. The Sanitary District rates, as determined by the rate schedule adopted by the Sanitary District Board, are now included on the Curran Gardner billing system.. The Water District has no authority to set sewer rates, nor to otherwise interfere in the operation of the Sanitary District. questions concerning the rates set by the Sanitary District, or questions about the operation of the Sanitary District should be directed to the Sanitary District offices at 528-0491.
The regular monthly board meetings will be held at Water District office at 7:00 P.M. on the second Tuesday of each month. Please call 217-546-3981 for more information.
Copyright © 2016
Curran Gardner Townships Public Water District